Chloride stress corrosion cracking (SCC) on the cooling water side of a 316L stainless steel exchanger tube. The cooling water contained approximately 400 ppm chlorides had been blocked in with the 350F shellside process still flowing. The black stringers are sulfide inclusions. 100X
If you have questions or need our depth of experience to help with your issues...
Call us: 281-556-8774
Email us: firstname.lastname@example.org
View all articles
covering updates on corrosion